Chigo Air Conditioning Repair Service in Haidian District, Beijing: E1 Failure Code Reason
Beijing Zhigao Air Conditioning After-sales Network Repair Changping District Service Areas: Chengbei Street, Nankou Area, Machikou Area, Shahe Area, Chengnan Street, Dongxiaokou Area, Tiantongyuan North Street, Tiantongyuan South Street, Huoying Street, Huilongguan Street, Longzeyuan Street , Shigezhuang Street, Yangfang Town, Xiaotangshan Town, Nanshao Town, Cuicun Town, Baishan Town, Beiqijia Town, Xingshou Town, Liucun Town, Shisanling Town, Yanshou Town. Beijing Haidian District Service Areas: Wanshou Road, Yongding Road, Yangfangdian Street, Ganjiakou Street, Balizhuang Street, Zizhuyuan Street, Xiaguan Street, Beitaipingzhuang Street, Xueyuan Road Street, Zhongguancun Street, Haidian Street, Qinglong Bridge Street, Qinghuayuan Street, Yanyuan Street, Xiangshan Street, Qinghe Street, Huayuan Road Street, Xisanqi Street, Malianwa Street, Tiancun Road Street, Shangdi Street, Wanliu District, Dongsheng District, Shuguang Street, Hot Springs Area, Sijiqing area, Northwest Mong area, Sujiayu area, Shangzhuang area. The main services are: air conditioning repair, cleaning, disinfection, installation, relocation, maintenance, security inspection, etc. If you need more information, please check the homepage. If you have any questions, please contact customer service.
The power-on operation indicator flashes and stops, and EI is displayed.
1): EI is displayed immediately after startup.
a: Check whether 2 or 3 of the six core wires are in the path. If there is no connection, it is an outdoor failure. Check whether the six-core cable is connected properly and whether the high voltage protector, overcurrent protector and overheat protector are in the path.
b: If the 2,3 bit path is an indoor control component failure.
2): Display EI after running for a period of time.
a: Check the working current, for example, when the current reaches 10.3A (3HP) or 13.2A (5HP), it acts as an overcurrent protector.
b: Check the system high pressure, such as protection up to 27KG for pressure protection
Chigo Air Conditioning Maintenance in Mentougou District, Beijing: Knowing the Maximum Current of the Compressor
Chigo Air Conditioner Repair in Haidian District, Beijing: Automatic mode of air conditioner can save
Chigo Air Conditioning Repair, Changping District, Beijing: Noise Failure of Air Conditioner Indoor Unit
- Causes and maintenance of water leakage in Chigo space in Mentougou District, Beijing
- Chigo Air Conditioning Repair Service in Haidian District, Beijing: E1 Failure Code Reason
- Water leakage at the air outlet of Zhigao air conditioner indoor unit in Mentougou District, Beijing
- Chigo 285, 325, 388, 418 wall-mounted air conditioner fault code table
- Three minutes after the start of Chigo inverter air conditioner, the red fault light is on.
- Chigo air conditioner shuts down for one minute after startup
- Chigo air conditioner KFR-36G / W on-hook not cooling
- Chigo Air Conditioning After Sales Center: Chigo Air Conditioning E4 Fault Code Repair
- Chigo air conditioner is turned on for 5 minutes to protect it from failure.
- Chigo air conditioning fan running compressor does not work